Programming your Victron MultiPlus inverter charger with the VE Configure program
The Victron MultiPlus inverter/charger is very programmable. It can be set up for different battery types, it can be set up to work in parallel or in split phase systems, it can also be set up to start a generator or it to run in quiet mode. It is especially programmable for use with Lithium Ion battery systems. There are various methods of programming, the principal method at the moment is by hooking it up to a computer with the aid of the Mk3USB interface. That requires a PC and a copy of the free VE Configure program which can be downloaded from the Victron Website.
Part 1 of this Blog Post described the proceedure for doing this. Now in this blog post we are going to talk about the setings themselves. As before we are referring in the text to the US version of the 12/3000 MultiPlus officially known as the MultiPlus 12/3000/120-50 120V VE.Bus
I have to confess that I dont know what all the settings are for. I am only writing about the ones I know. As time goes on I will figure out the uses for the other ones. Please feel free to add your comments in the place below and I will continue to update this article with your help.
2. General Settings
The first set of setting are in the General tab and are pretty self explanatory. Here is what this tab looks like by default:
Frequency: You can select the frequency that the inverter will operate on, the choices are 50 Hz, typically used in Europe, and 60 Hz typically used in the US. By default the US version of the MultiPlus will come set to 60 Hz. Note that this wont change the incoming frequency so when running on shore power it will pass through whatever frequency is incoming. When inverting it will go with whatever setting you selected.
Shore Limit: This is the limit of power that can come in to the MultiPlus and is the sum of the pass through power and the power used for charging the batteries. As the pass through power nears the limit you set the amount of power used for charging will automatically decrease to keep the power within the allowed limit. If your boat or RV has a 50 Amp dock service you should set this to 50 Amps (the default), If you have a 30 Amp service then you should set it to 30 Amps, and for those more rare installations where 15 Amps is the shore power service you should set it for 15 Amps. The aim here is to set this up so you wont blow the breaker on the dock. Note that if you plan on using the Power Assist feature that defines the minimum acceptable setting for shore power. We will cover that in more detail when we get to the Power Assist feature.
Shore Limit Override: If you have the Digital Multi Control and you check the "overruled by remote" box you can adjust the shore limit on the fly. That is helpful if you have an RV that sometimes plugs into a 15 Amp service and sometimes plugs into a 30 Amp service. See image below:
In this example above the Digital Multicontrol has set the shore power input limit at 16 Amps. This is done by turning the knob below the digital display
Dynamic current Limiter: I have to admit that I didnt know what this does so I had to look it up. This is what it does: This feature is intended to reduce load impacts on low-power generators, such as portable inverter technology models. These generators may be unable to respond to sudden load impacts. By activating the limiter, the PowerAssist function of the MultiPlus will absorb the change in load and transfer it smoothly to the generator, giving it time to react. The default setting for this is off.
Enable Battery Monitor: If the MultiPlus is the only source of charge to the batteries and the only draw then it can function as a basic battery monitor because it counts what went in and counts what comes out. This kind of installation is used where the purpose of the system is to provide backup power for essential equipment when the grid goes out. I dont have any experience of this kind of installation so I cant say any more about it. You would have to have a Color Control GX or Venus GX connected in order to be able to view the information generated. I dont know if the new VE Bus Bluetooth Dongle will be able to show this information but I imagine it will eventually if it doesnt already.
The grid setting doesnt apply much in the US because at the time of writing the MultiPlus is not certified for use as a grid tie inverter in the US. There is however one important setting on this page that you should pay attention to. Here is what the tab looks like by default:
The image above shows the default settings of the grid page. The box to accept wide frequency range is checked by default. The AC low and high disconnect and AC low and high connect are pretty obvious. I dont really see where it would be appropriate to change these. The UPS function is an important one to note though. UPS stands for Uninterruptable Power Supply and when that box is checked the idea is that the MultiPlus can instantly start inverting in the event of an interruption in the shore power. The switch over is so fast that devices like computers continue working without interruption. The UPS function means that the MultPlus must keep track of the incoming shore power and follow it exactly. If the incoming power is a small generator and gets distorted when the loads are high it can become impossible for the MultPlus to stay in sync with it. If the MultiPlus cant keep in sync it stops charging. If this happens unchecking the UPS box will usually eliminate the problem and allow the MultiPlus to continue to charge batteries.
The next tab we come to is the inverter tab. The default settings are shown below.
Inverter Output Voltage: This is by default set to 120 Volts and I dont see any reason to change it, but if you bought one of the European MultiPlus's that was by default set to 230 Volts and wanted to change it to 240 Volts this is where you would do it.
Ground Relay: This is a specific function that relates to the Autotransformer that we wont go into in detail here. I will just explain though that by default when the inverter is the source of power it connects ground and neutral together, which defines which of the outputs is neutral and which is live. When operaing on shore power there is no connection between ground and neutral on board the boat or vehicle.
Low Voltage shut down and low voltage restart: These by default are set to ridiculously low values so everyone should adjust these. By default they will run your battery totally flat. If you set the shut down voltage higher you will help protect your battery. Those of you with Lithium Ion batteries will be particularly interested in these settings as they can be used to prevent over discharge of the Lithium Battery. The exact setting you choose will depend on your battery but 12 volts would be a good starting point for low voltage shutdown. There has to be a difference between the low voltage shut down and the low voltage restart to stop the inverter turning on and off repeatedly. When the voltage gets low and the inverter shuts off the battery voltage will recover somewhat as soon as the load is removed and if the low voltage restart voltage is not set high enough it will start right back up again and the cycle will repeat.
DC voltage pre-alarm: You can set an alarm to let you know the voltage is getting low. If you have a Color Control GX the alarm will display on the screen. If you dont you would have to add an audible beeper of some sort. We will come to that later.
Power Assist: Power assist is the feature that allows the inverter to assist in starting loads. This is useful if you have a small generator and are trying to run an air conditioner. The inverter will assist the generator in starting the air conditioner and once it is running will cut back out and let the generator do all the work. This feature is on by default, I would suggest you turn if off unless you need it. Note that if it is enabled you might need to review the wire sizes you use in the installation since the output current from the MultiPlus can be greater than the input current. I found this video of the power assist function someone made to demonstrate this in action. Using Power Assist adds limits to the acceptable range of shore power current as discussed earlier. This article on current limits explains it better than I could.
Enable AES: AES stands for Automatic Economy Switch and is a way to reduce power consumption at low loads. There are two options, neither of which are enabled by default. The first option is called Modified Sine Wave and fiddles with the sine wave output to reduce comsumption at low power. If you set it for 60 Watts and you connect a 50 Watt light bulb it will burn dimmer when AES is enabled. Im not sure this option sounds that exciting to me especially since I went to the trouble of getting a true sine wave inverter to begin with. The second option is much more useful to my mind. In search mode the inverter stays off but once every second or two turns on momentarily to see if there is a load connected. If there is it turns fully on. You can set the level of load required to trigger it to turn fully on.
The charger page is where you get to match the parameters of your batteries to the output of the MultiPlus and is the page most users will be interested in tweaking. You will see that there are quite a number of presets already entered and by selecting a battery type it automatically selects the presets. You can then go on and make individual adjustments to any of the parameters. You can also make your own battery type. Here is what the tab looks like by default:
Most of these settings are self explanatory. In most cases the charge curves will adjust as you change the settings. Note that by default the maximum charge current is set to 90 Amps even though the maximum allowed is 120 Amps
Stop after excessive bulk: This will stop the bulk charge phase after 10 hours, you should probably check that box unless you have enormous batteries that would take more than 10 hours in bulk
Battery Charge Curve: The standard setting is ‘Four-stage adaptive with BatterySafe mode’. A detailed description is in the User manual Section 2
Enable Weak AC: This is one you dont want to check unless you need to because it will limit the maximum charge available. Weak AC allows the charger to accept very distorted input.
6. Virtual Switch and Assistants
I am going to deal with these in the next blog posts. The Assistants are a series of "Apps" that you can use to control additional functions. The Virtual Switch is another version of the same thing with less options. You cant mix and match, if you are going to use these its one or the other. The screenshot below is just to give you an idea of what the Assistants can be used for:
You dont need to tweak every setting but here are a few you should definitely look at:
- Set the AC current limit to match the shore power service you have
- Set the inverter low voltage shut down to a level that protects your batteries from over discharge, that means you also have to reset the start up voltage and the pre-alarm voltage
- Set the battery type or adjust the charge voltages to suit your battery
- Set the AES search mode to save power when no load is connected
- If you have a small generator take a look at the UPS function, the Power Assist function and the Dynamic Current Limiter
More blog posts in this series can be found below
- Installing your Victron MultiPlus Inverter Charger
- Demo Lithium Battery System - the details
- Demo Lithium Battery System
- Programming your Victron MultiPlus inverter charger with the VE Configure program - Part 1 - The Procedure
- Programming your Victron MultiPlus inverter charger with the VE Configure program - Part 3 - "The Assistants"
- Testing your Lithium Ion battery system
- Lithium Battery Installation - example from Sailbits.Com